- Module saves parameterisation permanently, even in the event of a power failure.
- Galvanically isolated RS-485 interface with pluggable screw terminal.
- Project planning and automatic generation of the EDE file required for BACnet via the WiNet-SW-01 software Wildeboer-Net.
- Up to 2500 data points per gateway possible.
A WiNet-GW gateway enables the Wildeboer-Net system to be connected to various open communication protocols. Protocols can also be operated simultaneously from a gateway. This enables monitoring and control of the connected fire dampers and other system participants from a central control station.
With BACnet, Modbus, LON and KNX the most commonly used bus protocols are supported. The data points to be transmitted via gateway can be conveniently defined via the central operating unit of the system without the need for separate software or a web browser.
Which system functions are to be visualised or controlled in detail can be flexibly defined via the central control unit or the WiNet software on an on-site PC. A total of three gateways are available in two variants each with 200 and 1,000 data points. The gateways communicate via Ethernet with the subnet controllers of the control system. For example, status messages from fire dampers can be forwarded or the shut-off devices can be opened and closed by actuator via the building management system. The communication system automatically creates the EDE file required for data exchange with BACnet after configuration, which ensures smooth connection of the system.